Goodman Company of Fayetteville, Tenn., is recalling about 210,000 air handlers sold in the U.S. and Canada.
The pull-out disconnects may not disable power to the air handler, posing an electrical shock hazard to individuals servicing the units.
The company has received reports involving six units at two locations of the air handlers remaining powered when the disconnect handles were removed. No injuries have been reported.
This recall involves Goodman air handler models AWUF and ACNF (A = Air Handler; W = Wall Mount; C = Ceiling Mount; U = Unpainted; N = Uncased; F = Flowrater).
The recalled air handlers are most often installed in apartment and condominium units and are used with heating and cooling systems to provide climate control. The AWUF model units are wall mounted, while ACNF model units are ceiling mounted.
The recalled air handlers have serial numbers beginning with 1511, 1512, or 1601 through 1610. The serial number is located on the label found by removing the wall panel (for AWUF units) or ceiling panel (for ACNF units).
The air handlers, manufactured in the U.S., were sold at Goodman heating and cooling equipment dealers nationwide from November 2015, through October 2016, for between $300 and $600 per unit. Apartment complexes, townhouse and condominium associations and individuals then generally purchased a bundled product including the unit, the installation and ancillary parts and supplies.
What to do
Consumers should immediately contact Goodman for a free inspection and free repair. Goodman is contacting all known commercial owners directly.
Consumers may contact Goodman toll-free at 888-386-2075 from 8 a.m. to 5 p.m. (ET) Monday through Friday or online at www.goodmanmfg.com and click on “Air Handler Product Recall” at the top of the page for more information.